The HyDip LCD is a simple weatherproof display unit for use with large tanks containing liquid.
It has a display screen showing volume of liquid (litres), a button to wake it up, and a built in overfill buzzer visible on one end plate.
The LCD should be fixed somewhere convenient on the tank, and connected to the HTG or HFT device which will measure the liquid level.
The HyDip LCD, showing 1) front plate, 2) display, 3) wake up button, 4) built in overfill buzzer, 5) weatherproof cable gland, 6) buzzer end plate, and cable gland end plate.
Although HyDip HTGv1 and HFTv1 devices have their own display, so that readings can be taken at the site of the tank, they need to be housed in a weatherproof (e.g. IP65 rated) enclosure.
For convenience, a HyDip LCD level display unit can be connected to your HyDip device and attached outside the enclosure to give you easier visibility of tank levels.
The HyDip LCD is weatherproof and can be sited outside.
It should be located somewhere convenient to find and easy to see. It needs to be close enough to the weatherproof cabinet with the HyDip device to run a cable to it.
You'll need to turn on HyNet in the online control panel to enable communications between the HyDip device and the LCD unit:
- Log into your HyDip online control panel
- In the folder tree on the left (or via the map dashboard) select the device
- Select the Devices view, then the System tab, and make sure you're in the Configuration tab
- Among the options you will see 'Enable HyNet'. Using the drop-down, switch this to Enabled and click Save.
To see the number of litres inside the tank, simply press the button on the display. After 20 seconds it will turn itself off to conserve energy.
If the overfill alarm is triggered, the buzzer sounds and the display flashes a warning message.
Power and performance spec
The LCD gains its power from the HyDip controller device. These specs are provided for your convenience.
Nominal supply voltage
12V … 24V DC ±10%
Battery supply voltage
6V DC ±25%
Battery supply current
150mA max, 10mA typ
0°C ... 40°C
Ingress protection rating
max 48V AC/DC, max 1A
External battery operation
At least 1000 hours
battery 6V, 10Ah, one LCD unit
Internal battery operation
At least 30 minutes
Resistive type 1kΩ / 2kΩ
overrun indicated as 1kΩ resistance
Although it is possible to power the HyDip LCD directly from the HyDip controller battery, external 12VDC power is recommended wherever possible. Some features are not available when external power is not available, including those for external horn, tank level control, current readout and pulse frequency.
Updated 45 minutes ago